Section 115 of the CFC, Pipeline setbacks, is added to read as follows:
115 Pipeline setbacks.
115.1 Pipeline setbacks. For purposes of this section “high pressure transmission line” is a natural gas pipeline operating at two hundred and fifty pounds per square inch or greater. A gas main or transmission line is a natural gas pipeline operating at sixty pounds per square inch or less.
115.2 No portion of a structure including accessory buildings and pools may be built within fifty feet of a high pressure transmission line with thirty-six inches of cover.
115.3 No structure may be built within forty feet of a hazardous liquid pipeline bearing refined product, with forty-eight inches or more of cover.
115.4 No habitable portion of a structure may be built within thirty feet of a crude oil pipeline operating at twenty percent or greater of its design strength.